Important Notice: This item is final sale and non-returnable.
The Wallbox Power Module controls up to six zones of light and will operate the following sources with a continuous Square Law dimming curve or on a full conduction non-dim basis:
- Incandescent li>
- LED1, 2
- Tungsten Halogen
- Electronic Low-Voltage (ELV)3
- Magnetic Low-Voltage (MLV) Transformer
- Metal Halide/High Pressure Sodium Switched
- Neon/Cold Cathode
- Lutron Tu-Wire Electronic Fluorescent Dimming Ballasts
- Approved LED and CFL lamps / fixtures
- Up to 64 DALI compliant output devices (devices must comply with IEC/EN 60929) can be addressed and grouped into zones (LQRK-WPM-6D and LQR-WPM-6D only).
|Power||120 V~ 50/60 Hz,|
220?240 V~ (non CE) (HQRJ-, LQRJ- and LQR- models only) 50/60 Hz,
230 V~ (CE) (LQRK- and LQRQ- models only) 50/60 Hz
|Typical Power Consumption||7 W; 0 Power Draw Units (PDUs).|
The Wallbox Power Module is not powered from the link, Pin 2
should not be connected. Typical Power Consumption test conditions:
all loads off, button LED on.
|Regulatory Approvals||UL, CSA, FCC, IC, SCT (HQRJ-, LQRJ-, and LQR- models only),|
CE (all other models), TRA (LQRK- models)
|Environment||Ambient operating temperature: 32 ?F to 104 ?F (0 ?C to 40 ?C).|
Ambient operating humidity: 0-90% humidity, non-condensing.
Indoor use only
|Communications||Wired (HomeWorks QS only) - Low-voltage type IEC PELV/NEC|
Class 2 wiring connects Wallbox Power Modules to processor. Each
HomeWorks QS processor has two configurable links. Wallbox Power
Modules communicate with the processor via the QS link or RF link.
RF (RadioRA 2 and HomeWorks QS): Lutron wireless Clear Connect
|ESD Protection||Tested to withstand electrostatic discharge without damage or memory loss, in accordance with IEC 801-2.|
|Surge Protection||Tested to withstand surge voltages without damage or loss of operation, in accordance with IEEE C62.41-1991 Recommended Practice on Surge Voltages in Low-Voltage AC Power Circuits|
|Power Failure||Provides 10-year power failure memory: Automatically restores lighting to levels prior to power interruptio|
|Mounting||Installs in a standard 4-gang U.S. wallbox, 3½in (89 mm) deep is strongly recommended. Always allow at least 4½ in (114 mm) clearance above and below the module to provide adequate space for cooling. Wallplate snaps on with no visible means of attachment.|
|Line Voltage Wiring||Each line voltage terminal can accept one 12 AWG (4.0 mm² ) wire.|
|IEC PELV/NEC Class 2 QS System Low-Voltage Wiring (HomeWorks QS only)||System communication uses low-voltage wiring. Wiring can be daisy-chained or T-tapped. Wiring must be run separately from line/mains voltage. IEC PELV/NEC Class 2 wiring link requires: Two 18 AWG (0.75 mm²) conductors for control power. One twisted, shielded pair of 22 AWG (0.34 mm2 ) for data link. Available from Lutron, P/N GRX-CBL-346S; check compatibility in your area. Total length of control link must not exceed 2000 ft (610 m)|
Payment & Security
Your payment information is processed securely. We do not store credit card details nor have access to your credit card information.